Servers, CPUs, storage and other hardware used in large data centers generate heat by converting electrical energy into thermal energy. To prevent them from overheating and causing failures or data loss, data centers need sufficient cooling and ventilation. This is the only way to ensure the reliable and fault-free operation of a data center.
The cooling of data centers causes enormously high energy costs. Around 30% of the energy consumption of a data center, which is not generated by the actual IT hardware, is accounted for by the fans used for cooling. The correct selection of the fans used can therefore make a significant contribution to reducing the operating costs of a data center.
Modular fan arrays are often used to supply and distribute the air and to remove the heated exhaust air. Since free cooling requires the removal of a large amount of heat without additional cooling, a high volume flow rate must be implemented with low back pressure. The operating points are typically in the right-hand are of the characteristic curve. Fans and fan wheels for general air conditioning and ventilation systems are not suitable for energy-efficient cooling of data centers, as their maximum efficiency lies in the left-hand range of the fan curve.
The new Data Center Cooling fan wheel from punker has been specially developed for supply and exhaust air in data centers where very high volume flows at low pressure are required. The new Data Center Cooling fan wheel achieves a significantly higher efficiency than competitor products in this application area. The use of this fan wheel thus enables savings in the operating costs of a data center. Another positive side effect is the reduction in noise emissions.
- Energy-efficient fan wheel enables savings in operating costs
- Very high efficiency facilitates achievement of FEI specifications
- Compact construction allows space-saving system design
- Easy installation and maintenance thanks to low weight
- Low noise emission due to optimized airfoil blades
- Data Center Cooling
- Data Center Air Handlers (CRAH)
- Fan arrays
- Supply air / Exhaust air in data center
- Plug fans
- Precision air conditioners (CRAC)
|Sizes||3 diameters, one width|
|Diameters||22″ to 27″|
|Material of construction||aluminum|
Find out how the new Data Center Fan Wheel can help reduce the annual operation cost of data center cooling by up to $US 7,000 in our case study “Reducing the Ecological Footprint of Data Center Cooling”.